No unauthorized person shall uncover, make any connections with or opening into, use, alter or disturb any public sewer or appurtenances thereof without first obtaining a written permit from the Superintendent.
There shall be two classes of building sewer permits: for residential and commercial service and for service to establishments producing industrial wastes. In either case, the owner or his agent shall make application on a special form furnished by the Village. The permit application shall be supplemented by any plans, specifications or other information considered pertinent in the judgment of the Superintendent. A permit and inspection fee of $10 for a residential or commercial building sewer permit and $25 for an industrial building sewer permit shall be paid to the Village at the time the application is filed.
All costs and expenses incident to the installation and connection of the building sewer shall be borne by the owner. The owner shall indemnify the Village from any loss or damage that may directly or indirectly be occasioned by the installation of the building sewer.
A separate and independent building sewer shall be provided for every building, except that where one building stands at the rear of another on an interior lot and no private sewer is available or can be constructed to the rear building through an adjoining alley, court, yard or driveway, the building sewer from the front building may be extended to the rear building and the whole considered as one building sewer.
Old building sewers may be used in connection with new buildings only when they are found, on examination and test by the Superintendent, to meet all requirements of this chapter.
The size, slope, alignment and materials of construction of a building sewer and the methods to be used in excavating, placing of the pipe, jointing, testing and backfilling the trench shall all conform to the requirements of the Building and Plumbing Code or other applicable rules and regulations of the Village and shall be subject to the approval of the Superintendent. In no event shall the diameter of such pipe be less than four inches, nor shall the slope of such four-inch pipe be less than one-fourth inch per foot.
Whenever possible, the building sewer shall be brought to the building at an elevation below the basement floor. In all buildings in which any building drain is too low to permit gravity flow to the public sewer, sanitary sewage carried by such building drain shall be lifted by approved artificial means and discharged to the building sewer.
No person shall make connection of roof downspouts, exterior foundation drains, areaway drains or other sources of surface runoff or groundwater to a building sewer or building drain which in turn is connected, directly or indirectly, to a public sanitary sewer or to a combined sewer after enactment of this chapter.
The connection of the building sewer into the public sewer shall conform to the requirements of the Building and Plumbing Code or other applicable rules and regulations of the Village or the procedures set forth in appropriate specifications of the ASTM and WPCF Manual of Practice No. 9. All such connections shall be made gastight and watertight. Any deviation from the prescribed procedures and materials must be approved by the Superintendent before installation.
The applicant for the building sewer permit shall notify the Superintendent when the building sewer is ready for inspection and connection to the public sewer. The connection shall be made under the supervision of the Superintendent or his representative.
All excavation for building sewer installation shall be adequately guarded with barricades and lights so as to protect the public from hazard. Streets, sidewalks, parkways and other public property disturbed in the course of the work shall be restored in a manner satisfactory to the Village.